- Ready to use PU foam in a 750ml can.
- Fire resistant in a joint (EN 1366-4).
- High filling capacity.
- Good adhesion on all surfaces (except PE, PP and PTFE).
- High insulation value, thermal and acoustic.
- Very good bonding properties.
- Gas- and flame proof up to 240 minutes in a joint.
- Water resistant (not watertight).
- Not UV-resistant.
- 12 months shelf life.
A fire rated one component, expanding polyurethane foam filler. Rapid curing. Excellent thermal and acoustic insulation properties. Expands 35-40 times its initial volume. Excellent primerless adhesion on most construction materials. Soudafoam FR is a PU-foam with fire retardant characteristics according to the European standard EN 1366-4. 12 months shelf life unopened and stored in dry and cool conditions (Between 5 and 25 °C), Upright storage is recommended.
||Stable foam, thixotropic
|Skin Formation (FEICA TM 1014)
|Cutting Time (FEICA TM 1005)
||Ca. 25 kg/m3
|Sound insulation (EN ISO 717-1)
|Thermal conductivity (λ) (EN 12667)
|Box Yield (FEICA TM 1003)
||750 ml yields ca. 30 l of foam
|Joint Yield (FEICA TM 1002)
||750 ml yields ca. 17 m of foam
|Shrinkage after curing (FEICA TM 1004)
||< 6 %
|Expansion after curing (FEICA TM 1004)
||< 1 %
|Expansion during curing (FEICA TM 1010)
||Ca. 86 %
|Compressive strength (FEICA TM 1011)
||Ca. 104 kPa
|Shear strength (FEICA TM 1012)
||Ca. 43 kPa
||-40 °C till +90 °C (cured)
- Sold as a box 12 x 750ml canisters.
- Installation of fireproof doors and windows. Sealing of fire retardant joints in walls and ceiling.
- As part of the ‘Soudal Fire Range’ assortment for penetration seals and joints.
- Sealing of all openings in roof constructions.
- Apply of an acoustic baffle.
- All foam applications in static joints.
Shake the aerosol can for at least 20 seconds. Put the adapter on the valve. Moisten surfaces with a water sprayer prior to application. For non-conventional substrates a preliminary adhesion test is recommended. Remove pressure from the applicator to stop. Fill holes and cavities for 1/3, as the foam will expand. Repeat shaking regularly during application. If you have to work in layers repeat moistening after each layer. Fresh foam can be removed using Soudal Gun & Foamcleaner or acetone. Prior to using the Gun & Foamcleaner, test whether surfaces are affected or not. Especially plastics and lacquer or paint layers can be sensitive to this. Cured foam can only be removed mechanically or with Soudal PU-Remover.
Can temperature: +5 °C - 30 °C
Ambient temperature: +5 °C - 30 °C.
Surface temperature: +5 °C - 35 °C
Standards and certificates:
- European Technical Approval Soudafoam FR - ETA 13/0280
- CE-marked (BCCA - EC conformity CPR)
- Joint Sound Reduction Test by IFT
- Various test and classification reports in various accredited testing institutes: IFT Rosenheim, ITB Poland, Warrington Fire Gent, Warrington Fire Australia, Efectis Netherlands, Efectis France, CSTB France, CSI Italy.
- Test results for penetration seals and/or joints with Soudafoam FR are freely accessible. This can be requested from our sales team Tel: +(0)1329 841416 or email email@example.com
Soudafoam FR conforms to the LEED requirements. Low emission materials: Adhesives & Sealants. SCAQMD regulation 1168. Meets USGBC LEED requirements v4.1: Low-Emitting Materials - Adhesives & Sealants regarding VOC content. For more information please contact the team on: Tel: +(0)1329 841416 or email firstname.lastname@example.org
We have technical representatives who provide assistance in the selection and specification of the products on this site and should be consulted for exact installation and product suitability. Ensure an early engagement with ourselves, designers, main contractor and specialist installers before any installation. Other trades and/or manufacturers may need to be consulted. For in-depth information, specification and technical advice please call our Head Office on Tel: +(0)1329 841416 or email email@example.com
All interested parties, designer, specifier, main contractor and specialist installers should provide access to allow the fire stopping seals to be regularly inspected and maintained, as well as records kept of such maintenance at minimum periods of 12 months, as required by the Regulatory Reform Order, and repaired if necessary. Reference should be made to ASFP TGD 17 – Code of Practice for the Installation and Inspection of Fire Stopping.
It is vital that those entrusted to design or install a fire stopping product have the necessary levels of competence to undertake the task professionally and thoroughly. The level of competency required will be commensurate with the expected complexity of the building. All designers must eliminate, reduce or control foreseeable risks that may arise during installation, construction or maintenance when preparing or modifying designs. Clients should ensure that the principal designer and principal contractor carry out their duties under CDM regulations. The ASFP foundation course in passive fire protection provides essential knowledge as part of demonstrating competency and understanding in this key fire protection specialism.
For further information on installation requirements please contact us to ensure the compatibility of this product, if in doubt please contact the technical team on: Tel: +(0)1329 841416 or email firstname.lastname@example.org
Health and Safety:
Take the usual labour hygiene into account. Always wear gloves and goggles. Remove cured foam mechanically. Never burn away. Consult label and material safety data sheet for more information. When vaporizing (for example with a compressor), additional security measures will be required. Use only in well ventilated areas. Please see (SDS) Safety Data sheet - This can be requested from our sales team on: Tel: +(0)1329 841416 or email email@example.com
Download and review any of the following information: