- CE Marked and UL-EU Accreditation.
- Fire Resistance Testing to EN 1366-3 : 2009.
- The pipes tested include PVC, PP, HDPE and PE, please refer to the test certification.
- Fire resistance testing through flexible wall and rigid floors and walls.
- Resistance to fire classification EN 13501-2.
- For internal use.
The Astro X Series CE Pipe Wrap are designed and tested to seal service penetration apertures containing plastic pipes using thermoplastic composites based on graphite intumescent technology.
Developed to provide a high volume expansion and pressure seal during a fire. The Astro X Series CE Pipe Wrap offers EI120 tested to EN1366-3, the maximum diameter being 200mm, the ultra thin design of Astro X Series CE Pipe Wrap ensuring that they can be installed in to the tightest of locations.
Astro X Series CE Pipe Wrap can be installed in flexible wall, rigid wall, rigid floor constructions and with Batt systems. They are compatible with polypropylene (PP), polyethylene (PE) and polyvinylchloride (PVC) pipes.
Astro X Series CE Pipe Wrap is used around combustible pipes to form a penetration seal used to reinstate the fire resistance performance of wall and floor constructions, where they have been provided with apertures for the penetration of combustible pipe services.
Astro X Series CE Pipe Wrap include an intumescent component incorporated into a lightweight PVC carrier bag to close any gaps and joints and provide a closure of combustible pipes when heated and to prevent the passage of fire.
*For specific details please refer to the test certification.
We have technical representatives who provide assistance in the selection and specification of the products on this site and should be consulted for exact installation and product suitability. Ensure an early engagement with ourselves, designers, main contractor and specialist installers before any installation. Other trades and/or manufacturers may need to be consulted. For in-depth information, specification and technical advice please call our Head Office on Tel: +(0)1329 841416 or email firstname.lastname@example.org
All interested parties, designer, specifier, main contractor and specialist installers should provide access to allow the fire stopping seals to be regularly inspected and maintained, as well as records kept of such maintenance at minimum periods of 12 months, as required by the Regulatory Reform Order, and repaired if necessary. Reference should be made to ASFP TGD 17 Code of Practice for the Installation and Inspection of Fire Stopping.
It is vital that those entrusted to design or install a fire stopping product have the necessary levels of competence to undertake the task professionally and thoroughly. The level of competency required will be commensurate with the expected complexity of the building. All designers must eliminate, reduce or control foreseeable risks that may arise during installation, construction or maintenance when preparing or modifying designs. Clients should ensure that the principal designer and principal contractor carry out their duties under CDM regulations. The ASFP foundation course in passive fire protection provides essential knowledge as part of demonstrating competency and understanding in this key fire protection specialism.
Please refer to the ETA/UL-EU sheet for fields of application for this product. For further information on installation requirements please refer to the pipe manufacturer data and wall specification to ensure the compatibility of this product, if in doubt please contact the technical team with services and wall specification on Tel: +(0)1329 841416 or email email@example.com
Download and review any of the following information:
Certification/Fire Test Reports:
CE Marked Documents
'DoP's are 'Declaration of Performance'
'CoC's are 'Certificate of Constancy of Performance'
'TDS' are 'Technical Data Sheet'
'ETA's' are 'European Technical Assessment Sheet'
'UL Documentation' are 'UL - EU Certificate'