- Astro X Series CE Pipewrap UL
- Astroflame Pipe Wrap on a Roll - CE Marked.
- Astroflame X Series CE Pipe Wrap UL is supplied on a 25m roll - cut to size on site.
- Certifire Approved
- Tested on a wide range of plastic pipes: PVC , PP , HDPE & PE pipes
- Tested in accordance with EN 1366-3 : 2009
- Classified in accordance with EN 13501-2
- Developed to provide a high volume expansion and pressure seal during a fire.
Astro X Series CE Pipe Wrap UL offers EI120 tested to EN1366-3, the maximum diameter being 200mm. Ultra thin design enables installation in the tightest of locations. Can be installed in flexible wall, rigid wall, rigid floor constructions and with Batt systems. Compatible with polypropylene (PP), polyethylene (PE) and polyvinyl chloride (PVC) pipes. Tested with end capping configurations that cover U/C & C/C pipes.
- 25m roll - cut to size on site.
We have technical representatives who provide assistance in the selection and specification of the products on this site and should be consulted for exact installation and product suitability. Ensure an early engagement with ourselves, designers, main contractor and specialist installers before any installation. Other trades and/or manufacturers may need to be consulted. For in-depth information, specification and technical advice please call our Head Office on Tel: +(0)1329 841416 or email firstname.lastname@example.org
All interested parties, designer, specifier, main contractor and specialist installers should provide access to allow the fire stopping seals to be regularly inspected and maintained, as well as records kept of such maintenance at minimum periods of 12 months, as required by the Regulatory Reform Order, and repaired if necessary. Reference should be made to ASFP TGD 17 – Code of Practice for the Installation and Inspection of Fire Stopping.
It is vital that those entrusted to design or install a fire stopping product have the necessary levels of competence to undertake the task professionally and thoroughly. The level of competency required will be commensurate with the expected complexity of the building. All designers must eliminate, reduce or control foreseeable risks that may arise during installation, construction or maintenance when preparing or modifying designs. Clients should ensure that the principal designer and principal contractor carry out their duties under CDM regulations. The ASFP foundation course in passive fire protection provides essential knowledge as part of demonstrating competency and understanding in this key fire protection specialism.
Download and review any of the following information:
Certification/Fire Test Reports:
CE Marked Documents
'DoP's are 'Declaration of Performance'
'CoC's are 'Certificate of Constancy of Performance'
'TDS' are 'Technical Data Sheet'
'ETA's' are 'European Technical Assessment Sheet'