- Fire rated ceiling air valves - inlet and extract types.
- 60 Minutes Fire Rating in Solid Timber Joist Floor/Ceilings Constructions.
- 30 Minutes Fire Rating in Metal Web Joist and I-Beam.
- Timber Joist Floor/Ceiling Constructions.
- No maintenance required.
- Meets requirements of Approved Document B.
- Simple to install.
- Highly cost effective.
Astroflame’s Fire Rated Air Valves are a unique and cost effective fire rated solution where recessed ceiling air valves are to be installed in fire rated floor/ceiling constructions. In a fire situation, the integral intumescent material rapidly expands to seal off the air valve to help maintain the fire resistance rating of the ceiling. This limits the risk of fire and heat spread throughout the building.
The Astro FR Ceiling Valve are available in all common sizes for both Extract and Inlet. The Fire Rated Air Valve is installed as normal with air flow through the air valve unaffected. The product requires no maintenance after installation. The Astro FR Ceiling Valve suitable for domestic homes, as well as apartments, hotels and other multiple occupancy buildings where fire ratings exist.
- Sizes: 100mm diameter - Extract Valve.
We have technical representatives who provide assistance in the selection and specification of the products on this site and should be consulted for exact installation and product suitability. Ensure an early engagement with ourselves, designers, main contractor and specialist installers before any installation. Other trades and/or manufacturers may need to be consulted. For in-depth information, specification and technical advice please call our Head Office on Tel: +(0)1329 841416 or email email@example.com
All interested parties, designer, specifier, main contractor and specialist installers should provide access to allow the fire stopping seals to be regularly inspected and maintained, as well as records kept of such maintenance at minimum periods of 12 months, as required by the Regulatory Reform Order, and repaired if necessary. Reference should be made to ASFP TGD 17 – Code of Practice for the Installation and Inspection of Fire Stopping.
It is vital that those entrusted to design or install a fire stopping product have the necessary levels of competence to undertake the task professionally and thoroughly. The level of competency required will be commensurate with the expected complexity of the building. All designers must eliminate, reduce or control foreseeable risks that may arise during installation, construction or maintenance when preparing or modifying designs. Clients should ensure that the principal designer and principal contractor carry out their duties under CDM regulations. The ASFP foundation course in passive fire protection provides essential knowledge as part of demonstrating competency and understanding in this key fire protection specialism.
For further information on installation requirements please confirm compatibility with your application, if in doubt please contact the technical team with your ceiling specification on Tel: +(0)1329 841416 or email firstname.lastname@example.org
Download and review any of the following information:
No reviews have been left for this product, be the first to leave a review