- A heavy duty automatic door seal by Raven RP70Si
- Durability tested to over 1,000,00 cycles without failure.
- Available in various sizes to meet your requirements
The RP70Si automatic seal is the fully mortised version of the RP38Si door seal. It is a heavy duty door bottom seal which is spring loaded to lift clear of the floor as soon as the door leaf is opened by a few millimetres.
The seal is operated automatically by pressure against the door jamb on the adjusting screw. It seals when the door closes and retracts automatically when door is opened. It is self leveling.
When using RP70si door bottom seal, the door must be a minimum of 45mm thick and of suitable construction for mortising this seal. It is reversible for left or right handed operation.
Note: For double doors, plain meeting stiles are required.
RP70Si has been tested for durability ~ 1,000,000 cycles completed without failure.
- Location: Single or double, butt hinged doors., minimum thickness 45mm.
- Min/Max Gap: 3mm to 13mm.
- Fixing Method: Fully mortised, can be adjusted, escutcheon plates provided.
- Seal Material: Silicon rubber (SE) (charcoal colour)
- Replacement Seal: RP338si.
- Seal Sizes (mm): 610mm. Seals cut back to exact size, 300mm min. Longer lengths to special order.
- Standard finish: Anodised Satin Clear.
We have technical representatives who provide assistance in the selection and specification of the products on this site and should be consulted for exact installation and product suitability. Ensure an early engagement with ourselves, designers, main contractor and specialist installers before any installation. Other trades and/or manufacturers may need to be consulted. For in-depth information, specification and technical advice please call our Head Office on Tel: +(0)1329 841416 or email firstname.lastname@example.org
All interested parties, designer, specifier, main contractor and specialist installers should provide access to allow the fire stopping seals to be regularly inspected and maintained, as well as records kept of such maintenance at minimum periods of 12 months, as required by the Regulatory Reform Order, and repaired if necessary. Reference should be made to ASFP TGD 17 – Code of Practice for the Installation and Inspection of Fire Stopping.
It is vital that those entrusted to design or install a fire stopping product have the necessary levels of competence to undertake the task professionally and thoroughly. The level of competency required will be commensurate with the expected complexity of the building. All designers must eliminate, reduce or control foreseeable risks that may arise during installation, construction or maintenance when preparing or modifying designs. Clients should ensure that the principal designer and principal contractor carry out their duties under CDM regulations. The ASFP foundation course in passive fire protection provides essential knowledge as part of demonstrating competency and understanding in this key fire protection specialism.
For further information on installation requirements please refer to the door manufacturer data to ensure the compatibility of this product, if in doubt please contact the technical team on: Tel: +(0)1329 841416 or email email@example.com
Download and review any of the following information: