- Classified in walls and floors of concrete, brick, gypsum etc.
- Suitable for cables, bundled cables, cable racks, cable trays, steel, copper, alupex and plastic pipes.
- Simple to apply leaving a very smooth finish.
- Please Note: NOT Suitable for Pizza Ovens, BBQ Bases, any types of ovens, fire places etc.
- No priming necessary prior to application in most building material substrates however metal services in contact with the seal must be corrosion protected.
- Suitable for most surfaces, included concrete, bricks, Leca, steel, plastic etc, but not suitable to fitting of doors or in service openings that involve movement.
- The product is certified for use in walls but it is recommended to use Astro PFP FR Boards for these applications.
- Fully set within 1 hour.
- The fire performance specification of the compound has been derived when the seal has been left to cure for 1 month.
Astro PFP FR EX Mortar is a dry white powder consisting of inorganic compounds and perlite.
When mixed with water, the compounds form a highly thermally insulating fire sealing compound to prevent the spread of fire and smoke through openings in fire rated walls and floors, including openings formed around building service penetrations.
Astro PFP FR EX Mortar will also maintain the acoustic design performance in walls and floors. Astro PFP FR EX Mortar expands approx. 1% by hydraulic action during curing ensuring a very tight seal around the service penetrations and the surrounding opening apertures.
Astro PFP FR EX Mortar is easy to sand or drill. The compound dries to an off-white colour which may be painted.
|Single sided cast = 50 mm thick as linear seal
||Rw 64 dB
|Double sided cast = 25 mm thick as linear seal
||Rw 64 dB
|Single sided cast = 50 mm thick as large seal
||Rw 48 dB
|Double sided cast = 25 mm thick as large seal
||Rw 48 dB
Astro PFP EX Mortar has been tested at BM Trada (UKAS accredited); according to EN ISO 10140-2:2010.
Resistance to Fire:
|Flexible walls comprise gypsum, masonry, aerated concrete or concrete
||Up to 2400 mm wide by 1200 mm high blank seal with double sided 25mm Astro PFP FR EX Mortar on 25mm cast board
||EI 120 (E 120)
|Rigid walls comprise masonry, aerated concrete or concrete, within walls or between the head of walls and the soffit of floor slabs
||Up to 2400 mm wide by 1200 mm high blank seal with single sided 50mm Astro PFP FR EX Mortar on 50mm cast board
||EI 120 (E 180)
|Up to 2400 mm wide by 1200 mm high blank seal with single sided 100mm Astro PFP FR EX Mortar
||EI 240 (E 240)
|Rigid floors comprise aerated concrete or concrete within floors or between floors and walls
||Up to 2400 mm by 1200 mm blank seal with 50mm Astro PFP FR EX Mortar on top of 50mm cast board
||EI 180 (E 180)
|Up to 2400 mm by 1200 mm blank seal casted with 100mm Astro PFP FR EX Mortar
||EI 240 (E 240)
The cast board comprise stone wool with density = 150kg/m3.
Please read the Installation Instructions before usage.
- Astro PFP FR EX Mortar is an off-white colour and available in 20 L bags.
- 10 L pail also available please contact us
We have technical representatives who provide assistance in the selection and specification of the products on this site and should be consulted for exact installation and product suitability. Ensure an early engagement with ourselves, designers, main contractor and specialist installers before any installation. Other trades and/or manufacturers may need to be consulted. For in-depth information, specification and technical advice please call our Head Office on Tel: +(0)1329 841416 or email email@example.com
All interested parties, designer, specifier, main contractor and specialist installers should provide access to allow the fire stopping seals to be regularly inspected and maintained, as well as records kept of such maintenance at minimum periods of 12 months, as required by the Regulatory Reform Order, and repaired if necessary. Reference should be made to ASFP TGD 17 Code of Practice for the Installation and Inspection of Fire Stopping.
It is vital that those entrusted to design or install a fire stopping product have the necessary levels of competence to undertake the task professionally and thoroughly. The level of competency required will be commensurate with the expected complexity of the building. All designers must eliminate, reduce or control foreseeable risks that may arise during installation, construction or maintenance when preparing or modifying designs. Clients should ensure that the principal designer and principal contractor carry out their duties under CDM regulations. The ASFP foundation course in passive fire protection provides essential knowledge as part of demonstrating competency and understanding in this key fire protection specialism.
Please refer to the ETA sheet for fields of application for this product. For further information on installation requirements please refer to the manufacturer of the services and the wall/floor specification to ensure the compatibility of this product, if in doubt please contact the technical team with services and wall/floor specification on Tel: +(0)1329 841416 or email firstname.lastname@example.org
Download and review any of the following information:
Certification/Fire Test Reports:
CE Marked Documents
'DoP's are 'Declaration of Performance'
'CoC's are 'Certificate of Constancy of Performance'
'ETA' European Technical Assessment Sheet
'TDS' are 'Technical Data Sheet'